People who live in urban environments might hardly ever envision using a well system as their primary source for water – but for those living in more rural and remote areas, it may be their only option.
According to a survey done by the US Census American Housing Survey, an estimated 13 million across the United States use private wells as their source for water (EPA).
Modern private well water systems have come leaps and bounds in efficiency and reliability as compared to older methods of ancient and even recent history. And while the establishment of municipal water systems will continue to provide water to hundreds of thousands and even millions of people in larger cities, there are undeniable advantages to owning a private well system for those in more remote areas and for the homestead owner.
In this article, we will discuss:
- The Advantages of Owning a Private Well Water Pumping System
- Basic Understanding of Groundwater
- Components of a Well Water System
- The Mechanics Behind How a Well Pump Works
- Important Things to Consider Before Starting a Well Water System
- Basic Maintenance Tips
Well Water Benefits and Advantages
The upfront cost of drilling and installation may prove to be a large financial investment, but for those dedicated to a more permanent homesteading lifestyle, it is an investment well worth the cost. Unlike homeowners in large cities who pay for monthly tap water service, homeowners who access water from their well system owe nothing – groundwater is literally free.
Other than the cost of the initial installation service and parts, the only cost a well owner would need to be aware of are maintenance costs and the use of electricity required to power the pump.
By relying on your own private access to groundwater, you eliminate the need for a municipal service to treat and distribute water to your home. While city tap water services adhere to strict sanitation guidelines, much of the beneficial minerals in groundwater are removed. Furthermore, additional chemicals such as fluoride are often added to the water supply without the public's consent.
In extreme cases, hundreds of miles of aging city water pipes and infrastructure can corrode long before a replacement plan is in place. As in the case of Flint, Michigan, thousands of residents suffered from illnesses due to a contaminated water supply (Glenza, 2018). With a privately owned well, the supply is entirely in the owner's control.
Water from the ground has undergone nature's most stringent purification process. After being thoroughly distilled through evaporation and precipitation, water flows through underground aquifers collecting minerals as it passes through layers of rock.
These minerals such as magnesium, calcium, and sodium are necessary for basic human function and add a natural, pleasant taste to the water. During its strict purification process, city water services often remove more of the beneficial minerals than what's necessary, leaving behind a nutrient-deficient, bland-tasting water.
Understanding the Groundwater Beneath You
Before understanding how a well water system works, it's best to understand where the water comes from.
Groundwater is the water found beneath the Earth’s surface which is renewed via precipitation when rain water or water from other forms of precipitation move downward to fill up the cracks or spaces in soil and rocks. Groundwater makes up almost all the water on Earth except ocean water and frozen water, accounting for around 95% of all fresh water.
Lakes, rivers and other surface water make up 3% of all fresh water. The renewal of groundwater depends on various environmental conditions. Groundwater naturally undergoes filtration, but it can get contaminated when it encounters the earth’s surface. Thus, groundwater needs to be protected from pollutants (NGWA).
Water exists underground in what are known as aquifers. Aquifers consist of layers of rock and soil which allow water to flow through their small pores. Groundwater can move from one aquifer to another. In general, groundwater follows permeable pathways within individual aquifers from point of recharge to point of discharge.
When a well is dug, drilled, or bored, the sole purpose is to reach far enough into the aquifer so that water can be accessed and pumped out. Because the location of aquifers and the amount of water in them are rough estimates at best, it is difficult to be certain exactly where and how deep and well needs to be dug.
Read Our Related Article: Best Well Pressure Tank Brands
Most Common Types of Wells
In order for groundwater to be accessed from the surface, the surface of the earth needs to be dug deep enough so that it reaches the aquifer. The hole that is created is known as a well. The three most common types of wells are drilled wells, driven wells, and dug wells.
Most modern wells are drilled wells. These wells are constructed by cable tool (percussion) or rotary (air or hydraulic) drilling machines.
Drilled wells penetrating unconsolidated material which consists of granular material such as sand, gravel, and clay require casing and a screen to prevent sediment from flowing in which can result in a collapse. The space around the casing also needs to be sealed with grouting material as water draining toward outside of the casing from the surface can contaminate the water in the well.
The grouting material can be made up of either neat cement or bentonite clay. Drilled wells can be more than 1,000 feet deep, thus a submersible pump is often used to push water to the surface.
Driven wells are relatively simple to construct and reasonably priced. These types of wells are dug vertically by driving a small-diameter pipe into shallow water-bearing sand or gravel.
A screen well point is usually attached to the bottom of the casing before driving to allow water to enter yet keep water-bearing formation in place.
Driven wells are typically around 30 feet deep when driven by hand and 50 feet deep when driven by machine. Thus, they can only tap shallow water and can be easily contaminated by nearby surface sources as they draw water from aquifers near the surface.
Read Our Related Article: Best Water Softeners for Well Water With Iron
Dug wells were historically dug by hand shovel or backhoe below the water table until the water coming in surpassed the digger’s bailing rate. The hole was then lined with stones, brick or tile to prevent the well from collapsing.
Modern dug wells are dug by power equipment and are usually lined with concrete tiles. These wells typically have large diameters, exposing a large area to the aquifer, and they can go deeper beneath the water table than hand-dug wells. Dug wells can obtain water from less-permeable materials such as fine sand or clay, however they are shallow and lack continuous casing which makes them prone to contamination from nearby surface sources. If the water table drops below the well bottom during a drought, dug wells may go dry.
Most modern wells are drilled as water can be accessed at much greater depths. However, dug wells are still constructed and driven wells are still common where geological conditions are suitable.
Well Water System Design and Components
The Well Pump
The well pump, or water pump, is the heart of the system. It is what pumps water upward and into the household or designated water system. The two most popular types of pumps used today are jet pumps and submersible pumps. Both pumps rely on centrifugal force in order to force water upward. Spinning rotors, known as impellers, create a vacuum which forces water upward through the well casing and into the distribution system. The type of pump required for a well system would depend on the depth of the well and the amount of water required for the household.
Jet pumps are placed above ground and lift water from the ground through a suction pipe which creates a vacuum with an impeller that drives water through a small nozzle. Because jet pumps use water to pump water, they first need to be primed with flowing water.
Shallow well jet pumps are used for wells that go down to a depth of 25 feet while deep well jet pumps typically go down 150 feet. Deeper wells would require a submersible pump (McDonald).
Submersible pumps have a much wider range in depth and can be used in wells as shallow as 25 feet and as deep as 400 feet. As the name implies, submersible pumps are submerged deep in the well just under the water level. Most of its energy is dedicated to pushing water upward rather than sucking water from above as in the case with jet pumps.
Submersible pumps are cylindrical in shape, housing the pump motor and a series of impellers which drives water up the pump into the drop pipe. Because of their efficiency, durability, and versatility in well depth, most modern well systems use submersible pumps over any other pump (McDonald).
The Pressure Tank
Pressure tanks are used to maintain water pressure throughout the distribution system and to store a reserve water supply so as to relieve the pump of continuous usage. The sizes range from around 40 gallons for domestic use to 21, 000 gallons or more for industrial use. In conventional pressure tanks, pressure is created by pumping water into the tank until air in the tank is compressed to typically 40, 50 or 60 psi (pounds per square inch). An air compressor ensures that the air pressure is maintained. When the valve is opened via a tap, the air pressure in the tank forces water out of the tank and into the pipes for distribution.
Pressure Switch & Control Box
Well pumps, especially submersible pumps, are not meant for around the clock usage. Continuous usage would cause unnecessary wear on the pumping mechanism and would rack additional electricity costs. The pressure switch and the control box work in conjunction with the pressure tank to measure the water pressure in the well system so that the pump is only used when the water pressure drops below a certain level.
Typical well systems have a water pressure range of 40-60 psi. When the water pressure drops below 40 psi, the pressure switch turns the pump on, bringing the water pressure back up within range. When the water pressure is at an adequate level, the pressure switch turns the pump back off.
Well casing, usually made of carbon steel, stainless steel or polyvinyl chloride (PVC), is a tube-shaped structure placed in a well to maintain the well opening spanning from the target ground water to the land surface. The casing prevents dirt from contaminating the water and keeps excess water out of the well. It also keeps out contaminants from less desirable groundwater. Some may use concrete, fiberglass, or asbestos cement to build well casing. However, the choice of material depends on the geologic formation. For example, steel is used where hard rock lies underground.
Well caps are placed on top well casing to keep out debris, insects and small animals. They are usually made of aluminum or plastic, and they include a vented screen to equalize the pressure difference between the inside and outside of the well when water is pumped from the well. To prevent overflows from contaminating the well, the cap should extend past flood level.
Well screens are filtering devices attached to the bottom of the well casing to prevent excess sediment from contaminating the well. Continuous slot, slotted pipe, and perforated pipe are the most popular well screens used. Well screens are built to suit the geologic condition with specified openings and holes to match the screen filtering capability. They are also designed to be placed within the saturated portion of the aquifer to prevent damage if the groundwater elevation drops.
Older well systems required that a large pit be dug in order that pipes were placed far enough underground so that they wouldn't freeze during winter time. But the pit design has proven to be quite hazardous and prone to contamination.
The modern pitless design allows for the casing to reach all the way up to the ground level. Pitless adapters are connectors that provide a sanitary seal between the well casing and the waterline. They are connected to the well casing below the frost line to divert water horizontally, preventing the water from freezing. A check valve may be fitted below the adapter to prevent water from flowing back into the well.
Mechanics Behind How a Well Water Pump Works
While jet pumps and submersible pumps are very different in design and mechanics, the concept behind their purpose is the same: pump water from the ground into the designated water system for usage. In explaining the mechanics behind how water is pumped from the ground and distributed throughout the system, we'll use the following setup as an example:
A private residence has a drilled well with a submersible pump in a pitless adapter setup, with a pressure tank and pressure switch inside the house.
- Most pressure tanks have a pressure range of 40 psi to 60 psi. When the water pressure is within this range (as indicated by the pressure gauge), the water pump is turned off, as there is a sufficient amount of water currently available in the system. For practical purposes, PSI can in fact be thought of in terms of the current volume of water rather than the actual pressure (more volume = higher pressure).
- As water is used throughout the house, whether it be from the sink, shower, dishwasher, or washing machine, the water pressure in the tank will naturally drop.
- When the pressure gauge indicates that the water pressure in the tank has dropped below the minimum range of 40 psi, the pressure switch will signal the pump to turn on.
- Some 200 feet below the ground, impellers in the submersible pump begin to spin rapidly, pushing water upward through casing and through the pitless adapter.
- As the water is forced through the water line and into the house, the pressure tank begins to fill gradually as indicated by the pressure gauge.
- Just as the pressure tank reaches the maximum psi of 60, the pressure switch will signal the pump to turn off, ceasing the flow of water into the system. The pressure will remain at this level until more water is used and it eventually drops. Once it drops below 40 psi, the pump kicks on and the cycle starts over.
Things to Consider Before Starting a Well Water Pump System
Know the Land
When either purchasing a home with a current well system in place or scouting the area for a place to build, it is best to be familiar with the land beforehand.
- Ask about other homeowners' wells in the area and whether they've had much success or trouble with their own system.
- Ask authorities about of the condition of the groundwater in the region and how deep they expect a well needs to be drilled, or whether the water level is known to be particularly low at certain times of the year.
- Be aware of the climate: rainfall, snow, flooding, and other things that may potentially cause problems for the well.
- Be aware of nearby factories or other factors that may pose a contamination risk.
Acquire all Necessary Permits
Each state and region will have its own required permits that would need to be applied for before well construction can begin, so do the research and be sure to have all of them. In most cases, contractors won't begin construction without all of the necessary permits.
Choose the Best Location for the Well Site
The location of the well is one of the most critical factors in determining its long term success and cleanliness. While choosing the best place for the most water yield is largely an estimate, choosing the best place for the least risk for contamination is much easier to determine.
- A rule of thumb is to always have the well site at a higher level of ground rather than a lower level of ground. In areas with heavy rainfall, rainwater will carry contaminants for the ground floor as in runs downhill. If the well site in an low-basin area where rainwater collects, there is a high risk that contaminants can enter the groundwater through the well.
- If the home has a septic tank, always choose a well site that is at a higher ground level than septic tank location and at a significant distance. Septic tanks always have the potential to leak so it's better that the contaminants move away from the well site rather than towards it
- Choose a location that has some distance between objects or places that can potentially disrupt or contaminate the well such as barns, livestock pens, streams or creeks, and septic tanks.
The Determine the Amount of Water the Household will Need
Knowing how much water your household will need will make it easier in determining the type of set you'll need. The average American uses 60-100 gallons of water per day which includes drinking, bathing, and washing clothes and dishes (NebGuide). Since well pumps vary in efficiency – measured in GPH (gallons per hour), calculating the average amount of water that your household will use can help determine the best type of well pump and pressure tank for your system.
Well Water System Troubleshooting, Maintenance, and Testing
It is important to maintain well systems regularly to prevent costly and inconvenient breakdowns. An annual well maintenance check is recommended, including a bacterial test. The annual checkup involves visual inspection of the wellhead, the well system components and other equipment to discover issues that could affect the water quality. The water should also be inspected if there is a change in taste, odor or appearance. Wells may need cleaning if the water is cloudy or contaminated with suspended matter, the water has developed an odor or taste problem, the water tests positive for biological activity or there has been a decrease in the well’s capacity.
Additional tests should be performed for production rate, static water level – the distance from the ground level to the top of the water in the well, and drawdown – the difference between the static water level and the level of water during pumping. These tests derive information which can be used to forecast the long-term yield of the well. Most households require a yield of 6 to 12 gallons per minute.
Additional Practical Considerations and Tips
- Don’t try to service your own well. Consult qualified professional water well system contractors instead
- Practice preventive maintenance which is less costly in the long run
- Do your homework before getting a well maintenance check-up or service
- Keep away hazardous chemical such as fertilizer, pesticides and motor oil
- Always use certified water well drillers and pimp installers
- Regularly inspect the well cover or well cap to ensure it is in good shape
- Maintain a proper separation between your well, waste systems and chemical storage facilities
While the initial set up of a well water system can be time consuming, costly, and will require much inquiry on the homeowner's part, the long term benefits of private well ownership are undeniable. Private well ownership saves the cost of monthly water bills, it allows for independent control of one's water supply, and provides healthy, mineralized water for consumption. A well pump, whether it be a jet pump which sits above ground or a submersible pump which resides 200 ft below the surface, is the heart of the well system and a worthwhile investment for any homesteader.
Thank you for taking the time to read our article on answering the question: How Does a Well Pump Work? We'd love to hear your feedback in the comments section below. If you've found this article to be useful and are interested in learning more, be sure to sign up for our newsletter.
Clean Water Store. (2018, October 26). How well water pump and pressure systems work? | Clean Water Store. Retrieved from https://www.cleanwaterstore.com/blog/how-home-well-water-pump-and-pressure-systems-work/
EPA. (n.d.). Learn About Private Water Wells | US EPA. Retrieved from https://www.epa.gov/node/83091/view
Glenza, J. (2018, April 25). Flint crisis, four years on: what little trust is left continues to wash away. Retrieved from https://www.theguardian.com/us-news/2018/apr/25/flint-water-crisis-four-years-later
Home Assessment System. (n.d.). Protecting Your Drinking Water Well. Retrieved from http://www.miwaterstewardship.org/Portals/0/docs/MSUE%20Bulletins/HAS-Protecting.Your.Drinking.Water.Well.pdf
Illinois State Water Survey. (n.d.). Wells and Pumping Systems for Domestic Water Supplies. Retrieved from http://privatewellclass.org/Portals
McDonald. (n.d.). Pump Basics. Retrieved from https://www.rcworst.com/Shared/content/mfr/a_y_mcdonald_mfg_co/docs/a_y_mcdonald_pump_basics.pdf
Minnesota Department of Health. (n.d.). Well Owner's Handbook. Retrieved from http://privatewellclass.org/Portals/2/Documents
Neb Guide. (n.d.). Planning for Water Use. Retrieved from http://extensionpublications.unl.edu/assets/pdf/g2149.pdf
NGWA. (n.d.). Groundwater facts. Retrieved from https://www.ngwa.org/what-is-groundwater/About-groundwater/groundwater-facts
NGWA. (n.d.). Pumping Systems. Retrieved from https://www.ngwa.org/docs/default-source/default-document-library/groundwater/pumping-systems.pdf?sfvrsn=383c9317_2
NGWA. (n.d.). Well System Components – Wellowner.org. Retrieved from http://bcd.d13.myftpupload.com/basics/types-of-wells/well-system-components/
University of Arizona. (n.d.). Private Water Well Components. Retrieved from https://extension.arizona.edu/sites/extension.arizona.edu/files/pubs/az1486b.pdf
USGS. (n.d.). Ground Water and the Rural Homeowner. Retrieved from https://pubs.usgs.gov/gip/gw_ruralhomeowner/
Water Systems Council. (n.d.). Well Owner's Manual. Retrieved from https://www.watersystemscouncil.org/water-well-help/well-owners-manual/
Well Owner. (n.d.). Planning for a Water Well – Wellowner.org. Retrieved from http://wellowner.org/basics/planning-for-a-water-well/